Seccionador Tripolar, Break Isolator, Substation
|FOB Price:||US $11 / Piece|
|Min. Order:||1 Piece|
|Min. Order||FOB Price|
|1 Piece||US $11/ Piece|
|Payment Terms:||L/C, T/T, D/P|
- Model NO.: GW4-72.5
- Structure: Three-column Disconnector
- Operation: Manual
- Movement Mode: Horizontal Rotary Type
- Grounding: Single Ground
- Run: Turn the Horizontal
- Structure of Operating: Manual
- Brand: Oei Power
- Transport Package: Wooden Case
- Origin: China Nanyang
- Type: High-voltage
- Installation: Outdoor High-voltage
- Grounding Mode: Grounding
- Number of Poles: Three Pole
- Series: Three
- Common Model: Ist
- Certification: IEC IEEE
- Trademark: OEI Power
- Specification: IEC IEEE
- HS Code: 8535309000
IEC 129:1975: Alternating Current Disconnectors (Isolators) and Earthing Switches
IEC 60694:2002: Common Specifications for High Voltage Switchgear and Controlgear
BS 729: Hot dip galvanized coating on iron and steel articles
Isolator (Disconnector) - a mechanical switching device which provides, in the open position, an isolating distance in accordance with Electrical Safety requirements.
The isolator shall be suitable for continuous operation outdoors in tropical areas at altitudes of up to 2200m above sea level, humidities of up to 90%, average ambient temperature of +30ºC with a minimum of -1ºC and a maximum of +40ºC and heavy saline conditions along the coast.
4.2. DESIGN AND CONSTRUCTION
4.2.1 The Isolator, Solid Link shall be designed and constructed in accordance with IEC 129 and IEC 60694.
4.2.2 The isolating link shall be of the vertical opening, designed for single phase manual operation. It shall be easily removed and replaced by using a portable operating rod.
4.2.3 The isolating link shall incorporate double porcelain insulators to suit voltage requirements and mounted on hot dipped galvanised steel under base suitable for vertical mounting.
4.2.4 The isolating link shall be arranged so that each unit is mounted independently on an angle bracket. It shall be supplied complete with the angle bracket and accessories suitable for mounting on 'U' type steel channel. The drawings to be submitted shall indicate all the applicable mounting positions.
4.2.5 The isolator shall be designed such that in fully open position, it shall provide adequate electrical isolation between the contacts on each phase. It shall conform to the requirement as single point isolation for safety.
4.2.6 All steel parts shall be hot dip galvanized to BS 729. The minimum coating of galvanizing required is 80 microns.
4.2.7 The solid link shall be removable from the mounting by use of operating rod.
4.2.8 All current carrying parts of the isolator shall be made of high conductivity material.
4.2.9 The isolator shall be fitted with clamp connectors for Aluminium (ACSR) conductor of Aluminium (ACSR)conductor of up to 18.2mm diameter.
The rating of the complete isolator shall be as follows: -
Rated lightning impulse withstand voltage
Rated power frequency withstand voltage, dry
Rated normal current
Rated short time withstand current for 3 sec, min.
Minimum creepage distance of insulators